|MLA Citation:||Bloomfield, Louis A. "Air Conditioners" How Everything Works 16 Jul 2018. Page 2 of 2. 16 Jul 2018 <http://www.howeverythingworks.org/prints.php?topic=air_conditioners&page=2>.|
This temperature gradient has its origin in the physics of gases—when a gas expands and does work on its surroundings, its temperature decreases. To see why this effect is important, imagine that you have a plastic bag that's partially filled with valley air. If you carry this bag up the side of the mountain, you will find that the bag's volume will gradually increase. That's because there will be less and less air overhead as you climb and the pressure that this air exerts on the bag will diminish. With less pressure keeping it small, the air in the bag will expand and the bag will fill up more and more. But for the bag's size to increase, it must push the air around it out of the way. Pushing this air away takes work and energy, and this energy comes from the valley air inside the bag. Since the valley air has only one form of energy it can give up—thermal energy—its temperature decreases as it expands. By the time you reach the top of the mountain, your bag of valley air will have cooled dramatically. If it started at 20° C, its temperature may have dropped to 0° C, cold enough for snow.
If you now turn around and walk back down the mountain, the increasing air pressure will gradually squeeze your bag of valley air back down to its original size. In doing do, the surrounding air will do work on your valley air, giving it energy, and will increase that air's thermal energy—the valley air will warm up! When you reach the valley, the air in your bag will have returned to its original temperature.
Air often rises and falls in the atmosphere and, as it does, it experiences these same changes in temperature. Air cools as it blows up into the mountains (often causing rain to form) and warms as it flows down out of the mountains (producing dry mountain winds). These effects maintain a temperature gradient in the atmosphere that allows snow to remain on mountaintops even when it's relatively warm in the valleys.
The most effective modern absorption cycle refrigerators use a solution of lithium bromide (LiBr) in water. What enters the boiler is a relatively dilute solution of LiBr (57.5%) and what leaves is dense, pure water vapor and a relatively concentrated solution of LiBr (64%). The pure water vapor enters a condenser, where it gives up heat to its surroundings and turns into liquid water. To convert this liquid water back into gas, all that has to happen is for its pressure to drop. That pressure drop occurs when the water enters a low-pressure evaporator through a narrow orifice. As the water evaporates, it draws heat from its surroundings and refrigerates them.
Finally, something must collect this low pressure water vapor and carry it back to the boiler. That "something" is the concentrated LiBr solution. When the low-pressure water vapor encounters the concentrated LiBr solution in the absorption unit, it quickly goes back into solution. The solution becomes less concentrated as it draws water vapor out of the gas above it. This diluted solution then returns to the boiler to begin the process all over again.
Overall, the pure water follows one path and the LiBr solution follows another. The pure water first appears as a high-pressure gas in the boiler (out of the boiling LiBr solution), converts to a liquid in the condenser, evaporates back into a low-pressure gas in the evaporator, and finally disappears in the absorption unit (into the cool LiBr solution). Meanwhile, the LiBr solution shuttles back and forth between the boiler (where it gives up water vapor) and the absorption unit (where it picks up water vapor). The remarkable thing about this whole cycle is that its only moving parts are in the pump that moves LiBr solution from the absorption unit to the boiler. Its only significant power source is the heater that operates the boiler. That heater can use propane, kerosene, electricity, waste heat from a conventional power plant, and so on.
However, if the fans are directing the cold air in a way that makes you more comfortable without having to cool all the room air or if the fans are creating fast moving air that cools you via evaporation more effectively, then you may be experiencing a real savings of electricity.
To figure out which is the case, you'd have to log the time the air conditioner cycles on during a certain period while the fans were off and the thermostat set to 75 °F and then repeat that measurement during a similar period with the fans on and the thermostat set to 78 °F. If the fans significantly reduce the units runtime while leaving you just as comfortable, then you're saving power.
The Air Conditioners Home Page — Printer Friendly
The Complete Collection of Questions about Air Conditioners (2 prints, from oldest to newest) — Printer Friendly: